The slurry pump will shake during operation. What is the reason for the shaking of the slurry pump? What is the method to deal with pump body shaking? Let's introduce you.
1、 Reasons for shaking of mud pump body:
1. The equipment has been used for a long time, the pump is worn and aged, the impeller is greatly loose, the bearing is damaged or the bearing clearance is large.
2. When the mud pump pushes the water flow during operation, the accompanying vortex and cavitation will inevitably produce large vibration.
3. There are sundries in the pump inlet pipe, impeller and pump, the pump is not fixed firmly with the foundation, the resonance is strengthened, etc.
4. The quality of mud pump is not qualified, the rotor is unbalanced, the pump and motor shaft are not concentric, and the rotor and stator collide or rub.
2、 Disposal method of shaking of mud pump body
1. Install flexible base. In order to meet the increasingly stringent vibration control standard of sand pumping pump, it is undoubtedly the best choice to install Sui sex base and use spring vibration isolator.
2. Install spring vibration isolator. When installing spring vibration isolator for mud pump, pay attention to the selection of its style and deflection.
3. Install rubber vibration isolator. Rubber vibration isolators are generally made of neoprene and natural rubber. Generally, compact rubber shock absorbers are selected. For water pumps with light weight, shear rubber shock absorbers can be selected.
The above is the reason and treatment method of mud pump shaking introduced by Xiaobian. I hope you can understand it.